Doityourself.com forum has 250,000+ expert and beginner discussions in over 120 categories, so we highlight popular chats to help with related projects. This transcript has been easily edited.
Original Post: electrical outlet height
Guest – Visiting guest
Can anyone tell me if there is any electrical code that indicates how high up from the floor an electrical outlet (120v) must be. Does ADA have anything to do with it. This is for a basement remodel. Thanks
I do not know of any NEC requirements for minimum height. Under specific circumstances, they even allow them to be mounted on the floor. There are some limits to maximum height, such as 18 “above countertops, or 6-1 / 2 ‘above quality outdoors. But no minimum as far as I know.
As for the ADA, I could not tell you.
For new work, I should say that horizontal spacing really has specific requirements, mainly designed to reduce the need for extension cords I think, because many people have no sense at all when it comes to how many gizmos can be connected to a 16 gauge, triple cable, or whatever which is precisely a tripping hazard. NEC says that there should be no greater distance, measured along the wall (including around the corners) than 6 ‘to any vessel. In other words, if you have a recipe every 12 ‘, no plug-in you place anywhere in the room will need a cord longer than 6’ to reach the recipe.
The NEC also says that the distance “as far as possible” should be equal between the containers. You can walk 6 ‘in both directions from the edges of a doorway even if you add the width of that doorway making the space between the two larger than 12’. I guess the idea there is that you do not intend to put a floor lamp in the middle of a doorway so that the cord must reach beyond 6 ‘!
The problem with NEC is sometimes that if something is not specifically required or banned, you can read all 618 pages and never find it mentioned before realizing that NEC does not care. And then you doubt yourself and think that you may have skipped it, so you read through all 618 pages again. This can last for a month under the right circumstances, and then you will still find nothing about what you are looking for a decision on!
Generally, most containers are installed so that the bottom of the drawer is approx. 16 “over finished floor. General.
Hope it helps.
narrow man – Member
Use a standard 16 oz. straight hammer for the height of the container. This places the bottom of the drawer about 13 “above the floor.
For light switch, go 42 “to the bottom of the gearbox.
For worktops / switches, go 46 “to the bottom of the drawer. Thank you.
Wgoodrich – Visiting guest
There is no minimum height regarding inside a home. Even if a vessel is mounted in the floor with an approved floor vessel unit and within 18 “of the wall, this vessel is permitted to meet the requirements of the 6 ‘/ 12’ rule found in 210-52 for living rooms.
Now the maximum height is allowed and still use a vessel in a living room that meets the 6 ‘/ 12’ rule found in 210-52. The maximum height is 5’6 “above the floor as a maximum height for a vessel to be used that meets the 6 ‘/ 12’ rule.
thinman says an accepted practice, he points to the height of counter areas, good idea to listen so that the containers and switches do not land behind the back of the sink. Juice is approximately 18 “maximum above a counter plus there is a maximum below one counter to serve the counter area of 12” but the container is only allowed below the counter area if nowhere is available above the counter area.
Hope this helps!
DIY123 – Member
According to IFMA, the minimum height allowed for an electrical outlet according to ADA is 15 “.
hollett4704 – Member
In Canada it is 14 “to min. You can mount it higher if you want.
chandler – Former member
I hope that OP at some point in the last seven years could get its problem solved. Check the dates of the posts.
joed – Member
“In Canada it is 14” to the center min. you can mount it higher if you want. “
Can you give me code reference for this. The only thing I could find in my codebook from 1998 says that if they are over 1.7 m, they do not count the containers required along a wall.
franska277V – Member
That’s true, it’s a pretty old thread but I would lock it out, but somehow I think I’ll leave it open for now because it’s going to be a good reminder with any reader related to the ADA requirement as an update whether someone forgot it or not think in advance.
Joined NEC it almost parallel to it but it falls in both NEC and IBC so it should be very similar to what you have in your area.